Powerful rectangular mono color light fitting
– Seamless lighting with completely eliminated dots
– Compact light appliance design which stores attachment parts
|Product Name||–||Length||–||Light source color||–||Cover Type||–||Environment|
|N : Natural white
W : White
WW : Warm white 3500K
L30 : Warm white 3000K
L27 : Warm white 2700K
L24 : Warm white 2400K
|DF : Diffuser||I : Indoors|
|Luminaire efficacy(2700K)||74.7 lm/W||74.7 lm/W||74.7 lm/W|
|Light source color||O = Device inventory * = Equivalent|
|N||5000K||Ra 92||Ο||238 lm||Ο||1190 lm||Ο||2380 lm|
|W||4000K||Ra 92||Ο||238 lm||Ο||1190 lm||Ο||2380 lm|
|WW||3500K||Ra 93||Ο||230 lm||Ο||1151 lm||Ο||2303 lm|
|L30||3000K||Ra 94||Ο||222 lm||Ο||1113 lm||Ο||2226 lm|
|L27||2700K||Ra 93||Ο||215 lm||Ο||1075 lm||Ο||2150 lm|
|L24||2400K||Ra 93||Ο||199 lm||Ο||998 lm||Ο||1996 lm|
|Specification may be subject to change without announcement.
The optical data provided on the each product pages are for reference only; the data values are not guaranteed. Please use as reference materials for your planning.
Special order product size
General Specification | External dimensions
|Environment||Indoors (no condensation)|
|Max. length per circuit||3.3m|
|Material (body)||Polycarbonate, Aluminum|
|Attachments||Mounting parts 2pcs|
|Option parts||Mounting parts, Power supply cable, Joint cable|
|Mounting parts A|
Model No : LTH-PTA
|2 pcs included|
|2 pcs/1 bag|
Power supply cable 3M
Model No : CAD-3000-MCRN-I
1 pcs per circuit for connecting the LED fixture to power supply or dimmer driver
Joint cable 1M
Model No : CAD-1000-MCFC-I
Joint cable between two LED fixtures
Installing the product
Mark the center line for the LED fixture on the installation surface, then aligned the mounting parts using the line as the center point. Fix the mounting parts by screw supplied by installer (Pan head screw M5), then install the LED fixture on the mounting parts.
|To avoid the mounting parts being deformed, DO NOT over-screw the screws, use countersunk screw and install the LED fixture forcefully when the mounting parts are misaligned.
When using deformed Mounting parts, the LED fixture may drop from the Mounting parts. Make sure the LED fixture is fixed tightly after installation.
Mark the center line for the LED fixture on the installation surface, then aligned the mounting parts using the line as the center point. Fix the mounting parts by screw supplied by installer (Pan head screw M5), then install the LED fixture on the mounting parts. In order to prevent displacement,attach the mounting parts near the edge of the LED fixture.
|– Highly recommend not to recess on the wall
– To avoid the mounting parts being deformed, DO NOT over-screw the screws, use countersunk screw and install the LED fixture forcefully when the mounting parts are misaligned.
When using deformed Mounting parts, the LED fixture may drop from the Mounting parts. Make sure the LED fixture is fixed tightly after installation
System configuration diagram
- Max. connectable length depends on the wattage of the power supply.
- Max. length per circuit of Luci RECTA is 3.3m.
If it exceeds 3.3m, please split into multiple circuits.
- Max. distance from the power supply to the end of LED fixture is 10 m.
Direct horizontal surface light intensity distribution chart
Recommendend dimensions and illumination distribuitions